How do I change my gasket?
Door gaskets should be checked and cleaned regularly and replaced if damaged. To clean the gasket, wipe with warm soapy water and a soft cloth, ensuring it is completely dry before closing the door.
DO NOT use a sharp knife to clean or scrape the gasket. Damaged gaskets do not seal correctly and can increase the amount of electricity consumed, seriously affecting the efficiency and performance of the cabinet. Damaged gaskets are easily replaced. Simply pull out existing part and push new gasket into the channel (gasket retainer) at centre and work along, pushing gasket into the channel. Continue with additional three sides, pushing corners in last.
How do I put the cabinet into defrost manually?
On Millennium Controllers (The Half moon Logo around the controller) Hold in the 2 red Arrows together until the defrost light appears.
On Budget Controllers (Oblong Black Face) Press the Up and Down Arrows together until the defrost light appears.
I have CLN showing on the display screen
Switch off, switch back on and immediately press the I button. This again is the Clean Condenser Alarm reminder.
I have an alarm and flashing light on the squiggle snake symbol, what does this mean?
This is the Clean Condenser reminder. Press and hold symbol for three seconds to cancel. We would recommend that you carry out the cleaning condenser procedure outlined in your operating manual which can be found in the infocentre.
If I need to order a spare part who do I have to contact?
Contact our spares department direct on: 01553 817017
What information do I need to hand when ordering a spare part?
You will need to state the following: Company name, address, quotation reference - if you have already been quoted, if not a correct model and serial number, payment details - either cheque or credit card.
We do also ask for faxed orders so that we have hard copies of the customer’s order with all their details on.
What power supply is required for the blast chiller models WBCF30 and 40?
16 Amp that requires hard wiring into electrical connection.